Remote On-Line Diagnostic System to find a battery fault previously by remotely measuring a Cell Voltage, Cell Temperature, and Cell Impedance of UPS and Stationary Battery System.
- Measuring a cell internal resistance by injection of AC current on battery terminal.
- Measuring a Cell terminal voltage
- Measuring a Bus current by HALL CT
RU equipment : max 64 Cells available
MPU equipment : 7 RU, max 448 Cells available
Communication type : RS232, RS422, TCP/IP
Mode : Trend, Event, Real Time
Result : Time Chart, 2D, Report function
Analysis method : Trend Data pattern Analysis